Your guess is as good as mine…
Just a couple of brief items (relatively—you know how I do go on, but I will try) of interest. I don’t know that there’s a common theme besides an effort to anticipate in which direction the survey winds might blow in 2018:
- Previously in this space, I’ve mentioned the work of Matt Freije and his team at HCInfo as they have done yeoman’s (yeoperson’s?) work in the field of water systems management and the “fight” against In response to last year’s letter of intent by CMS to take a more focused look at how hospitals and nursing homes are providing appropriately safe water systems for their patients, Mr. Freije has developed a checklist to help folks evaluate their current situations and has posted the checklist online for comment, suggestions, etc. I’m having a hard time thinking that this might not become something of a hardship for folks arriving late to the party, so if you’ve not yet embraced poking around this subject (and even if you have), you’d do well to check out the checklist .
- A couple of inspection items relative to the ongoing rollout of the various and sundry changes wrought by the adoption of the 2012 Life Safety Code®, some of which have yet to migrate in detail to the accreditation organization publications (at least the ones that I’ve seen), but have popped up during recent CMS surveys:
- Make sure you fire alarm circuit breakers are clearly marked in red (check out NFPA 72 10.5.5.2 for the skinny on this).
- Make sure your ILSM/fire watch policy/process reflects the appropriate AHJs—you need to make sure that you know for sure whether your state department of public health, et al, want to be notified. They do in California, and probably elsewhere.
- In NFPA 25, chapters 5 and 13 indicate some monthly inspections of gauges, valves for condition, appropriate position (open or closed) and normal pressures—again, they’re not specifically listed in the accreditation manuals yet, but I suspect that they’ll be coming to a survey report near you before too long.
- A final note for the moment in this category, NFPA 70 (2011 edition) 400.10 indicates that “flexible cords and cables shall be connected to devices and to fittings so that tension is not transmitted to joints of terminals.” Keep an eye on power strips, particularly in your IT and communications closets for those dangling power strips (and some of them aren’t so much dangling as they are pulled across open spaces, etc. I suspect you know what I mean.) I know the folks who manage this stuff think that we are just being pains in the butt, but now you may have a little codified leverage.
- In my post a couple of weeks ago, I don’t think I played the personal protective equipment (PPE) card with sufficient gravity; part of folks’ understanding of the hazards of using chemicals is recognizing the importance of actually using appropriate PPE as identified on the product SDS. When you think about it, the emergency eyewash station is not intended to be the first line of defense in the management of exposures to chemical hazards, but rather what happens when there is an emergency exposure. If the use of PPE is hardwired into the process, then the only time they’ll need to use the eyewash equipment is when they do their weekly testing. At that, my friends, is as it should be.